SAN DIEGO COUNTY AIR POLLUTION CONTROL DISTRICT
RULE 260.115a - MONITORING OF OPERATIONS
(a) Except as provided in Section (d) of this rule, the owner or operator subject to this subpart shall maintain a record of the petroleum liquid stored, the period of storage, and the maximum true vapor pressure of that liquid during the respective storage period.
(b) Available data on the typical Reid vapor pressure and the maximum expected storage temperature of the stored product may be used to determine the maximum true vapor pressure from monographs contained in API Bulletin 2517, unless the Control Officer specifically requests that the liquid be sampled, the actual storage temperature determined, and the Reid vapor pressure determined from the sample(s).
(c) The true vapor pressure of each type of crude oil with a Reid vapor pressure less than 13.8 kPa (2.0 psia) or whose physical properties preclude determination by the recommended method is to be determined from available data and recorded if the estimated true vapor pressure is greater than 6.9 kPa (1.0 psia).
(d) The following are exempt from the requirements of this section: